VCMI IO chngs «R»«S»«T» OK - L3COMM_IO
Intermittent flashing red to green and vice versa and one comm card is making noise...
Flame Failure : Frame 6B Machine
Frame 6 B machines; Mark Vie . DLN-1 system , synchronized with grid. Partload operation Flame failure in Premix steady state .
Is it possible to create a counter for Starting System running hours counter ?
Rotational Direction of a Turbine Generator
Could you please help me clarify if the rotational direction of a turbine is always the same.
By Osama Arafa on 7 August, 2018 - 4:33 pm
This is a more than sufficient reply, I just would like to add some tiny facts: In the stator of...
Phase to earth voltages are heavily unbalanced
When we run the DG with neutral ungrounded, the phase to earth voltages are heavily unbalanced. And it is changing during the course of running.
By W.L. Mostia on 10 August, 2018 - 3:25 pm
Might you supply the actual voltage values you are talking about. In an ungrounded system, if you...
Generator breaker question
Will machine go on over speed?
DS200LDCCH1A AND DS200DCFBG1B Failing Continuously
EX2000 LDCC AND DCFB failing continuously
GE MK_V Turbine Not Responding to Load Command on Governor Control
Experiencing problems with a GE MK_V turbine control system. When load command reaches 63% while in governor control, load will not respond. Control has to be put in load limit mode to raise or lower load at this point.
on 6 August, 2018 - 1:21 pm
If this is a relatively new occurrence, not related to oil condition, it would seem that some input...
Fire Detection System Control Modules Suppliers
We need a supplier for Hi-Safe Rack3 Fire detection system control cards/modules.
GT13E2 Turbine Operation Manual
Looking for GT13E2 Turbine Operation Manual
Parallel Generator and Synchronization With Grid
Lingering questions running through my head about parallel generator and synchronization with grid.
By Papoo Sankaran on 8 August, 2018 - 3:54 pm
Explaining complex technical subjects in the simplest form using 'easy to understand analogies is...
Ge 9fa Unit During Running Got Tripped Due To Mark Vi Chanel R And T Failure
Ge 9fa Unit During Running Got Tripped Due To Mark Vi Chanel R And T Failure (2 out of 3)
Field excitation and fuel consumption variations causes different behaviours in power generation when generators are in parallel or in single
Any Standard or Guidelines for Spare Cores in Instrument Cables
We want to know any specific code or standards that highlight the spare cores for the control and AI,DI, RTD and TC cables to be left inside control cables.
What is the problem if run alternator less than required parallel cable in one phase.
By d on 1 August, 2018 - 5:54 pm
first get the electrical drawings for that installation, and get a qualified electrical specialist...
LVDT .7 V adjustment procedure?
PGT10 / GE10B1 - Flashback During Acceleration (Mark VIe control)
PGT10 - GE10B1, Speedtronic Mark VIe (old SUVIMAC II removed in 2014). Since the Hot Path Inspection, the machine trip on Flashback at 5200 rpm.
GT generator hydrogen purity drop
GT generator hydrogen purity drop
on 30 July, 2018 - 4:46 pm
To mitigate the effects of increased seal oil flow-rates causing decreased hydrogen purity, that...
By A. Sandoval on 28 July, 2018 - 11:14 pm
Today we looked a bit further into the H2 purity and discovered that the scavenging set point in...
DORIC Temperature Indicator
Posted by sultan Khan on 17 May, 2018 - 11:16 am
DORIC digital temperature indicator used in Mk 2 panel does not indicate any temperature value, but only flickers. It is a mv to temp. converter for "K" type thermocouple.
By Amar DAMENE on 30 July, 2018 - 1:39 pm
Hi..Khan, Sorry, Would you contact me by email or viber email@example.com viber:...
Why AFPCS value increasing during rain storm?
GT Lube Oil Tank Water Contaminate
Instruments affected in case of water contaminate observed inside Frame-V lube oil tank.
Mark VI Trip Log Question
I have a Mark VI turbine controls system with the windows seven update, and the trip logs quit running.