Turbine Failing to Ignite
After plant blackout, turbine fails to ignite.
Generator Seismic Probes MS5001
The gas turbine MS5001 tripped on high seismic vibrations. Both seismic vibration probes values (North and South) spiked simultaneously and caused tripping.
Exhaust Thermocouples Spread MS5001
The gas turbine installed on site ( Mark-VI) has 13 exhaust thermocouples. The unhealthy thermocouple's value (-17) is not being disregarded and spread value being shown is 426.3'C while the allowable value is 51.4'C
difference between stall and choke in compressors
Voltage Drop in Perkins Generator
Having a issue with voltage loss on Perkins genset.
Mark-V <LCC> CARD Replacement
Mark-V <C> <LCC> card EEPROM replacement.
How Electrostatics Field Effects the Vibrations
How vibration is effected by electrostatic fields, it causes mark on journal bearing as a result vibration shoot up.
15K Generac Guardian Ultra Source
Generator starts fine, however when you push in the choke it starts to over rev the engine and there is no power output.
Communication between PC and PIC16 using MODBUS protocol
What are the parameters to put in ASE2000?
By Modbus TCP Settings on 12 September, 2017 - 4:01 am
Hello David, Thank you for your input and apologies for the late reply. the ASE 2000 that...
What is base load temperature?
Starting Jaw Clutch Disengaging and Engaging During Ratcheting
After the shut down of our MS5001GE gas turbine, the ratcheting sequence has not be operating properly in the sense that the clutch disengages and engages.
Frame-V machine MOP discharge and Trip Oil pressure gradually dropping down.
By Chiranjeevi on 8 September, 2017 - 11:42 pm
CSA, Can u share your mail so that i can send to you the diagram. Or i will provide my mail...
Voltage Problem 3 Phase Generator
Need to adjust voltage each time I turn selector switch to different setting.
WHAT IS PURGE AIR AND WHAT IS OPERATION OF PURGE AIR
Critical Path and Governor Shutdown
Definition of Critical Path SD and Governor SD
Issues with Power Generation when in Sync with the Utility Supply
Issues with the power generated when in sync with the Utility supply.
By Wesley Boodram on 4 September, 2017 - 2:57 pm
Hi CSA/Saul, Some good news is that we got the opportunity to load the generator, and it was not...
System Inputs for Gas Turbines
Please, could anyone give me some idea about how to chose appropriate input variables for a gas turbine?
By sardar108 on 5 September, 2017 - 5:23 am
I am also interested in your documents please. Can you send it to me. Thanks firstname.lastname@example.org...
Functions of Servers provided with Mark-VIe
Have any Bailey experts replaced an Alpha Workstation?
Seal Oil/Hydrogen Differential Pressure
High generator seal oil flow, empty seal oil vacuum compartment, fluctuating differential pressure, high seal oil pump discharge pressure
Questions about MARK VI TMR
Questions about MARK VI TMR.
WorkstationST OPC DA Server
How does the OPC DA server work exactly with the workstationST
question regarding the operation of the gas turbines in islanding mode...
By Chiranjeevi on 30 August, 2017 - 7:19 am
Mark v guy, you mean to say that as the ambient changes, which will changes the air density and...
By Igho Anthony on 29 August, 2017 - 6:07 pm
A 2007 post helping me understand a problem 10years later!!! Bravo!!! My issue is that the grid...
Off base LO Skid Drain SOV 20QA-2
what is the purpose of warren pump Off base LO skid Drain SOV 20QA-2 in frame V machine.
Problem starting a 1MW diesel engine